Orchard Electrical Services
Your Cart is Empty
There was an error with PayPalClick here to try again
Thank you for your business!You should be receiving an order confirmation from Paypal shortly.Exit Shopping Cart
|Posted on November 26, 2012 at 3:52 PM|
I've just completed a job which, while extensive, should have been pretty straightforward. I say "should"; it would have been if the last electrician who worked on the house had been anywhere near competent.
When I began work in the house, I found more safety issues than I like to think about. The two worst were;
Seven (yes, SEVEN!) cables, including a cooker cable, all crammed inside a length of trunking that was only big enough for two or three at best. When I separated out the cables, the ones at the back were warm to the touch!
Inside the consumer unit, I found three circuits connected into one breaker. That's bad enough but before I even put a screwdriver to the breaker, two of the live wires lifted straight out!
To be honest, I'm actually amazed that the homeowners hadn't had a fire years ago.
Things like this make me so angry, not to mention ashamed on behalf of every competent electrician out there. Things like this are the reason that Part P was introduced, and why you should always use an Approved Contractor.
I wonder how many other bodge jobs the last guy perpetrated and how he sleeps at night?
Categories: Horror Stories